*7-Segment digital display.
*The pressure values and line pressure values of the cylinder group in the left-right can be monitored.
*Audio-visual alarm notiﬁcation.
*Manual and automatic adjustable working system
*In case of emergency, manual gas ﬂow is provided by by-pass system..
*Audio-visual status display and fault display.
*Alarm status is designed in accordance with HTM standards
*High pressure and low pressure alarm status are adjustable.
*The status of the plant can be monitored by the LED signals on the control panel.
*In case of emergency, manual gas flow is provided by by-pass system.
*The audible alarms can be set to silent mode.
Cylinder manifolds are an important element of gas management in hospitals. They ensure the supply with medical gases and control the gas pressure. The core of the system is the Gas Control Station.The manifold control system shall conform to ISO 7396-1 - Medical gas pipeline systems, NHS Health Technical Memorandum HTM 2022 and HTM 02-01.The manifold control system shall provide an uninterrupted supply of a specific medicalgas from equally sized high pressure cylinder banks via a suitable arrangement of pressure regulators, providing a constant downstream nominal pipeline gauge pressure of 400 kPa or 700 kPa. The entire system shall be 'duplexed' such that any single functional component failure will not affect the integrity of the medical gas supply. The manifold shall be supplied fully assembled and tested.
Automatic Manifolds provide a continuous supply of gas from two banks of cylinders by automatically changing to the standby bank when the duty bank has become depleted.